Montaggio Kit. Connettere il disgiuntore idraulico (2) alla caldaia come da figura. 2 assicurandosi di interporre le guarnizioni (1) e (3). Collegare al disgiuntore. Lastmanuals provides you a fast and easy access to the user manual IMMERGAS VICTRIX 75 KW. We hope that this IMMERGAS VICTRIX 75 KW user guide. 18 Red silicone O-ring (9,19×2,62). 19 Red silicone O-ring ( ,87×2,62). 20 Plastic “Immergas” nameplate.
|Published (Last):||9 July 2009|
|PDF File Size:||8.56 Mb|
|ePub File Size:||19.48 Mb|
|Price:||Free* [*Free Regsitration Required]|
Lastmanuals offers a socially driven service of sharing, storing and searching manuals related to use of hardware and software: If this document matches the user guide, instructions manual or user manual, feature sets, schematics you are looking for, download it now.
Victrix 75 buy in Kostanaj
Download immeggas complete user guide Ko. In any way can’t Lastmanuals be held responsible if the document you are looking for is not available, incomplete, in a different language than yours, or if the model or language do not match the description.
Lastmanuals, for instance, does not offer a translation service. Designated trademarks and brands are the property of their respective owners.
Detailed instructions for use are in the User’s Guide. As an Immergas customer you can also count on a qualified after-sales service, prepared and updated to guarantee constant efficiency of your boiler. Read the following pages carefully: Contact our area authorised after-sales centre as soon as possible to request commissioning.
To install possible coupling extensions on other fume extraction elements, proceed as follows: Fit the male end smooth of the exhaust pipe 2 up to the stop on the female end of the bend 1making sure that the internal ring 3 is fitted; this will ensure hold and joining of the elements making up the kit.
Ducting is an operation through which, within the context of restructuring a system and with the introduction of one or more special ducts, a new system is executed for evacuating the fumes of a gas appliance, starting from an existing flue or a chimney or a technical hole.
Ducting requires the use of ducts declared to be suitable for the purpose by the manufacturer, following the installation and user instructions, provided by the manufacturer, and the requirements vicctrix the standards. In any case, ducting operations must respect the provisions contained in the standard and in current technical regulations; in particular, the declaration of conformity must be compiled at the end of work and on commissioning of the ducted system.
The instructions in the project or technical report must likewise be followed, in cases provided for by the standard and current technical regulations. The system or components of the system have a technical life complying with current standards, provided that: The “VICTRIX 75” boilers installed in cascade and composed of 2 or 3 generators, can be joined by manifold to a single flue going the chimney.
However, for correct assembly of the kit the following indications must be taken into consideration.
Kit assembly Fig ; install and fit the various sections with fume damper and 3 up to the stop on the central hole of each single boiler. Fit the various bends with inspection and 6 on the relevant sections with damper from the shortest to longest so that the bend closest to the flue is the highest see figure abovethen fit pipe 7 on bend 4. The following checks and maintenance should be performed at least once a year – Clean the flue side of the heat exchanger – Clean the main burner.
Search for a user manual.